Thermal Conductivity Considerations in Ice Rink Design
Contrary to their simple appearance, ice rinks are highly specialized and meticulously planned facilities incorporating industrial refrigeration systems. Operating costs of ice rinks can be enormous, and the energy costs of running the cooling equipment can account for over 50% of the total operating budget of a rink. Under the ice surface is a system of layers starting with a concrete slab containing cooling pipes, which circulate a refrigerant such as brine to draw heat away from the ice surface and release it in a different area (Figure 1). This concrete structure has a large influence on the energy costs of the rink; the higher its thermal resistance, the lower the temperature of the brine, which in turn reduces the evaporation temperature and increases the energy needed to run the refrigeration system. Improving the thermal performance of this concrete slab could greatly enhance the energy efficiency of the rink. In 2014, Haghighi et al. from the Royal Institute of Technology in Sweden performed research using the Hot Disk Transient Plane Source thermal conductivity system with the goal of creating a concrete with a higher thermal conductivity than conventional concrete for use in ice rink floors.
Figure 1. Arrangement of layers typically present in the structure under the ice surface.
Haghighi et al. (2014) created their concrete by replacing the aggregate material used in the mixture, commonly sand or gravel, with highly thermally conductive iron ore. The novel concrete then underwent freezing and strength tests required for ice rink operations. The amount and exact type of iron ore used was in the process of patent application at the time of publication and was not detailed in the report.
Thermal conductivity and thermal diffusivity measurements of the concrete were performed with the Hot Disk TPS 2500 S, a state of the art thermal conductivity testing system capable of measuring thermal conductivity from 0.005 to 1000 W/mK in a temperature range between -160°C to 1000 °C. Haghighi et al. (2014) sandwiched a two-sided Hot Disk sensor between two pieces of concrete for testing (Figure 2). The set up was then covered to prevent any environmental factors from influencing the results (Figure 2). The same test method was used to test conventional concrete for use as a reference. A single sided sensor, the TPS-S, is also available for use with Hot Disk equipment (Figure 3). This sensor performs the same measurement as the two-sided sensor with only one sample piece, and is an excellent option for clients with samples that are difficult to cut or expensive to produce.
Figure 2. Photos from Haghighi et al. (2014) of the test set up they used to measure the thermal conductivity of concrete samples with the Hot Disk TPS 2500 S.
Figure 3. GIF showcasing the simplicity of thermal conductivity testing using the TPS-S.
Thermal Conductivity of Improved Concrete for Ice Rink Applications
Haghighi et al. (2014) discovered that the thermal properties of the iron ore concrete they had created were much improved from those of conventional concrete. Thermal conductivity had increased by 58.2%, thermal diffusivity by 15.5%, and specific heat by 37% (Table 1). These results indicate that this product could be highly useful in ice rink applications, as the improved conductivity and diffusivity will lower the thermal resistance of the slab and increase its ability to respond to temperature changes. Haghighi et al. (2014) did not stop their research with the creation of the specialized concrete, they also designed two alternative floor structures that could use this product while minimizing construction costs. Energy modelling with these designs showed that thermal efficiency was increased and operating costs were reduced.
Table 1. Thermal characteristics of conventional and experiment concrete obtained by Haghighi et al. (2014) using the Hot Disk TPS 2500 S.
Thermal Conductivity (W/mK)
Thermal Diffusivity (mm2/s)
Specific Heat (MJ/m3K)
This study is an interesting application of the Hot Disk TPS thermal conductivity equipment in concrete testing. The majority of concrete testing is performed with the goal of decreasing thermal conductivity in order to increase the thermal efficiency of concrete in building material applications. In this highly specialized application, the opposite result is the most energy efficient option. The large thermal conductivity measurement range of the Hot Disk TPS makes it a powerful tool that can provide accurate results in a variety of testing situations.
Learn More About Hot Disk Transient Plane Source (TPS)
The Hot Disk Transient Plane Source (TPS) technique allows for precise thermal conductivity measurement of a huge array of materials ranging in thermal conductivity from 0.005 to 1800 W/m∙K . TPS is capable of measuring bulk and directional thermal properties of solids, liquids, pastes and powders.
Introduction In 1990, Maurice Ward debuted his miraculous invention on the British TV show ‘Tomorrow’s World’ by demonstrating how an easily applied paint could protect an egg from cooking after being heated by a blow torch. To the amazement of all viewers, the egg...
The Building Envelope Insulative paint can be applied to the interior and the exterior walls of a building to increase the thermal insulation. Any structure that separates the outside and the inside of a building is called the building envelope which includes...
How thermal effusivity and additional thermal properties quantifies the touch/feel of automotive interiors Introduction The global automotive interior industry is one of increasing importance and has continued display steady growth patterns throughout the past decade....